Standard Practice for Sampling Two-Phase Geothermal Fluid for Purposes of Chemical AnalysisTranslate name
STANDARD published on 1.9.2020
Designation standards: ASTM E1675-20
Publication date standards: 1.9.2020
The number of pages: 9
Approximate weight : 27 g (0.06 lbs)
Country: American technical standard
Category: Technical standards ASTM
chemical analysis, fluid chemistry, geothermal resources, two-phase geothermal fluids,, ICS Number Code 75.020 (Extraction and processing of petroleum and natural gas)
|Significance and Use|
4.1 The objective of this practice is to obtain representative samples of the steam and liquid phases as they exist in the pipeline at the sample point, without allowing steam condensation or additional liquid flashing in the separator. A significant feature of the practice is the use of a cyclone-type separator for high-efficiency phase separation which is operated at flow rates high enough to prevent significant heat loss while maintaining an internal pressure essentially the same as the pipeline pressure.
4.2 Another significant feature of the practice is to locate the sampling separator at a point on the pipeline where the two-phase flow is at least partially stratified to aid in the separation process. It is neither necessary nor possible to pass representative proportions of each phase through the sampling separator to obtain representative samples. The separator is usually attached to an appropriately oriented port to collect each specific phase – normally on top of the line for steam and at the bottom for liquid. In some cases, piping configurations can generate unusual flow regimes where the reverse is required. If the ratio of one phase to another is not extreme, it may be possible to obtain representative samples of each phase from a horizontal port on the side of the pipeline.
4.3 This practice is used whenever liquid or steam samples, or both, must be collected from a two-phase discharge for chemical analysis. This typically includes initial well-testing operations when a well is discharged to the atmosphere or routine well production when a well discharges to a fluid gathering system and power plant. The combined two-phase flow of several wells producing through a common gathering system may also be sampled in accordance with this practice.
4.4 This practice is not typically employed when individual wells produce to dedicated production separators. In these cases, the separated steam and liquid at the outlet of the production separator is sampled in accordance with single-phase sampling methods (Specification ). It may, however, be used downstream of production separators when separator efficiency is expected to be very poor. In these cases, the method is used to remove the contaminating phase from the samples being collected.
1.1 The purpose of this practice is to obtain representative samples of liquid and steam as they exist in a pipeline transporting two-phase geothermal fluids.
1.1.1 The liquid and steam samples are collected and properly preserved for subsequent chemical analysis in the field or an off-site analytical laboratory.
1.1.2 The chemical composition data generated from the analysis of liquid and steam samples may be used for many applications important to geothermal energy exploration, development, and the long-term managed exploitation of geothermal resources. These applications include, but are not limited to, resource evaluations such as determining reservoir temperature and the origin of reservoir fluids, tracer-based measurements of production flow and enthalpy (TFT), compatibility of produced fluids with production, power generation and reinjection hardware exposed to the fluids (corrosivity and scale deposition potential), long-term reservoir monitoring during field exploitation, and environmental impact evaluations including emissions testing.
184.108.40.206 To fully utilize the chemical composition data in the applications stated in , specific physical data related to the two-phase discharge, wellbore, and geothermal reservoir may be required. Mathematical reconstruction of the fluid chemistry (liquid and steam) to reservoir conditions is a primary requirement in many applications. At a minimum, this requires precise knowledge of the total fluid enthalpy and pressure or temperature at the sample point. Fluid reconstruction and computations to conditions different from the sample collection point are beyond the scope of this practice.
1.2 This practice is limited to the collection of samples from two-phase flow streams at pressures greater than 70 kPa gauge (10 psig) and having a volumetric vapor fraction of at least 20 %. This practice is not applicable to single-phase flow streams such as pumped liquid discharges at pressures above the flash point or superheated steam flows. Refer to Specification for sampling single-phase geothermal fluids.
1.3 The sampling of geothermal fluid two-phase flow streams (liquid and steam) requires specialized sampling equipment and proper orientation of sample ports with respect to the two-phase flow line. This practice is applicable to wells not equipped with individual production separators.
1.4 The two-phase equipment and techniques described here are often the only way to obtain representative steam and liquid samples from individual producing geothermal wells. They have been developed to address common two-phase conditions such as:
1.4.1 Unstable production flow rates that have a large degree of surging,
1.4.2 Unknown percentage of total flow that is flashed to steam or is continuously flashing through the production system,
1.4.3 Mineral deposition during and after flashing of the produced fluid in wellbores, production piping, and sampling trains,
1.4.4 Stratification of flow inside the pipeline and unusual flow regimes at the sampling ports, and
1.4.5 Insufficient flash fraction to obtain a steam sample.
1.5 This practice covers the sample locations, specialized sampling equipment, and procedures needed to obtain representative liquid and steam samples for chemical analysis.
1.6 This standard does not purport to address all of the safety concerns, if any, associated with its use. It is the responsibility of the user of this standard to establish appropriate safety, health, and environmental practices and determine the applicability of regulatory limitations prior to use. 1.7 This international standard was developed in accordance with internationally recognized principles on standardization established in the Decision on Principles for the Development of International Standards, Guides and Recommendations issued by the World Trade Organization Technical Barriers to Trade (TBT) Committee.
|2. Referenced Documents|
Do you want to make sure you use only the valid technical standards?
We can offer you a solution which will provide you a monthly overview concerning the updating of standards which you use.
Would you like to know more? Look at this page.
Latest update: 2021-04-20 (Number of items: 2 442 933)
© Copyright 2021 NORMSERVIS s.r.o.